A three phase induction motor utilises three-phase alternating current electric power to supply electricity to the devices to which it connects. In the three-phase system, three circuit conductors deliver three alternating currents of the same frequency to a destination. Electric power distribution grids, large motors and large electrical loads utilise a three phase inductor system to deliver electrical power.
Other People Are Reading
Direct Online Starting
Direct online starting also known as across the line starting and full voltage starting, involves connecting each terminal of a three-phase induction motor to a separate line of a device. In this arrangement, the motor current is the same as the line current and the terminal voltage of the induction motor equals the line voltage. A disadvantage of the direct online starting method is that the stator draws a high current that can damage the windings of the three-phase induction motor. The direct online starting method can also cause a voltage drop or fluctuation that can affect devices along the line.
Wye and Delta Connections
In a wye or star connection, the windings of the induction motor connect from the supply phases to the neutral. In a delta or mesh connection, the windings connect between the supply phases. A wye connection creates higher voltage to the windings of the three-phase induction motor than a delta connection. A starter with the ability to utilise both star and delta connections, also known as a wye start delta run connection, initialises the three-phase motor using a wye connection then transfers to a delta connection when the motor reaches a set speed. A disadvantage of the star-delta connection is the reduction in voltage and the low starting torque that can have an adverse effect on devices or pumps that have a high breakaway torque. A star-delta connection is more complex than a direct online connection because it utilises a speed switch and timers. The induction motor requires a shock to start and another shock when the star-delta connection transfers from wye to delta. The wye-delta method is often convenient for partial acceleration.
Series Reactor Connection
A reactor in series with the terminals of the motor decreases the terminal voltage of the induction motor, decreasing the initial current. The impedance decreases as the induction motor accelerates until a bypass method makes the motor run at full speed and full voltage.
Variable Frequency Drive
A variable-frequency drive starts a three-phase induction motor at a frequency low enough to initialise a full-rated torque without an inrush of current. The low frequency increases the torque because it increases the impedance of the rotor circuit with slip frequency.
- 20 of the funniest online reviews ever
- 14 Biggest lies people tell in online dating sites
- Hilarious things Google thinks you're trying to search for