Wiring ganged dimmer switches is an easy project that even a beginner can complete successfully the first time. There are two types of incandescent dimmer switches available -- single-pole dimmers and three-way dimmers. You use the single-pole dimmer switch, like the single-pole toggle switch, to control a light from a single position. You use the three-way dimmer, like a three-way toggle switch, in conjunction with a second three-way toggle switch to control a light from two positions, or in conjunction with a three-way toggle switch and one or more four-way switches to control a light from three or more positions. You wire ganged dimmer switches the same way no matter which switch configuration you have.
Things you need
Non-contact voltage tester
2-gang cover plate
Ganging two single-pole dimmers
Turn off the branch circuit breaker. Use the non-contact voltage tester to verify that the circuit is safe. The non-contact voltage tester will beep loudly if there is still voltage present in the gang box.
Cut the stripped ends of the insulated wires in the gang box flush with their insulation. Good wire splices start with straight wire ends. In the case of new wiring, go to the next step.
Remove 1.8 cm (3/4 inch) of insulation from the ends of the insulated wires in the gang box. Use a scrap piece of the same size wire to adjust the cutting depth of the wire cutters. You want to set the depth to cut cleanly though the insulation without biting into the wire. "Ringing," cutting a groove around the wire, will weaken the wire and cause it to break. Ringing also reduces the wire's cross-section area increasing its resistance to the flow electric current. You want to avoid damaging the wire when stripping it, so take the time to get the cutting depth right.
Splice the three white, neutral wires together. Hold their stripped ends side by side and twist them together with a right-hand twist using the Lineman's pliers. Complete the splice by screwing on a wire nut.
Splice the green leads from the dimmer switches to the three bare copper wires in the gang box. Make this splice the same way you spliced the white, neutral wires together in the above step.
Splice the "Line" side leads of the dimmer switches to the black wire coming from the service panel. Splice the "Load" side lead from each dimmer switch to the black wire going to the light it will be controlling. Make sure the you do not reverse the dimmer leads marked "Line" and "Load." Reversing the leads can damage some electronic dimmer switches.
Secure the switches in the gang box and install the faceplate. Turn on the branch circuit breaker.
Ganging two 3-way dimmer switches
Follow Steps 1 to 6 from Section 1.
Splice the red and black "Load" leads to the "Traveler" wires continuing to the three-way or four-way switch. The circuit traveller wires are not polarised. It does not matter which load lead you connect to which of the circuit wires as long as they are coming from the same cable. Do not mix the travellers from one cable with those coming from the other cable. No damage will be done if you do, but the switches will not operate properly.
Repeat Step 7 from Section1.
Things you need
- Non-contact voltage tester
- Wire cutters
- Wire strippers
- Lineman's pliers
- Dimmer switches
- Wire nuts
- 2-gang cover plate